How to eliminate E8 error in Ferroli air conditioning?
- Error: E8
- Description: Flow detector error
- Solution: Check that all water circuit interception valves are completely open. 1. Check that the water filter is not clogged. If necessary, clean it with running water. 2. Check that the system is properly loaded with water and that it has no air pending purge. If necessary, purge the system of the system. 4. Check in the pressure gauge that the water pressure is> 1 bar. 5. Check that the pump speed is not too low and, therefore, does not guarantee sufficient flow. If necessary, increase speed. 6. Check that the expansion vessel is not broken. 7. Check that hydraulic circuit load losses are not too high for the pump (consult the total height of the water pump). 8. If the electric booster is installed, and this error occurs during the thaw phase, check that the Booster receives food (examine the power cables and verify if the protection devices have been activated). 9. Check that the pump protection fuse and the fuse present on the control card are not burned.
If you fail to solve the Ferroli Air Conditioning error, we recommend that you contact the technical service or specialist in air conditioners. These professionals can advise you on how to solve the problem effectively and safely.
Other error codes in Ferroli air-conditioning
How to eliminate PD error in Ferroli air conditioning? Error: PdDescription: Excessive temperature protection at the condenser exitCause: Solution: 1. Check that the panels that protect the battery during transport ...
How to eliminate PB error in Ferroli air conditioning? Error: PbDescription: Antifreeze protectionCause: Solution: After the antifreeze protection phase, the device will automatically resume normal operation. More tips If you ...
How to eliminate PP error in Ferroli air conditioning? Error: PPDescription: The water inlet temperature is higher than heated water outlet temperatureCause: Solution: 1. The connector of one of the ...